This paper uses the concept of the continuation power flow analysis used in voltage stability analysis. It uses the continuation load flow to plot the PV (pressure-volume)curves of an induction motor load. A neuro-fuzzy model of an induction motor load is used to represent an industrial load. In the subsequent predictor-corrector stages, the induction motors are increased to depict increment in loading. Different motor ratings are used in the investigation. The process starts at some base values of the system and lead to the critical point. Further, the reduced Jacobian is used to strategically locate the capacitor banks in the power system so as to effect maximum voltage improvement. In the case study, illustrative examples with the IEEE 30 bus system are shown.
Key words: Continuation load flow, induction motors, voltage stability, neuro-fuzzy
Copyright © 2022 Author(s) retain the copyright of this article.
This article is published under the terms of the Creative Commons Attribution License 4.0